Epoxy Resin Insulator
Medium Voltage Insulators
High Voltage Epoxy Resin Insulator
Vacuum Circuit Breaker
Epoxy Resin Bushing
Electrical Switchgear Components
Cast Resin Transformer
Copper Electrical Contacts
High Voltage Disconnect Switch
Zinc Oxide Lightning Arrester
Industrial Cable Ties
Electrical Conduit Plastic Pipe
High Voltage Indicators
Moulded Case Circuit Breaker
StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
FKN12-12RD Indoor Vacuum High Voltage Load Switch 3 Phase 12kV 1250A
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Rate Voltage||12kV||Frequency Voltage||42kV|
hv disconnect switch,
high voltage isolator switch
FKN12 High Voltage Indoor Vacuum Load switch with switcgear
The type FKN12-12RD high voltage indoor vacuum load switch and electrical comination is use for Three phase alternating current Concurrent 50HZ industrial power euipments , its can laod control and protect short current . Load switch is open-close load , closed current , and charging cables current . Electrical comination can close any current . There can be use by hand and power . FKN12-12RD is designed by drive type , light weight . Temperature is from 40 degree to -25 degree . Earthquake strength is 8 .
A load switch is an electrical switch between an isolation switch and a circuit breaker. It has a simple arc extinguishing device that can cut the rated load current and a certain overload current, but can not cut the short circuit current.
|Rated voltage (KV)||12|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||42|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||75|
Under the action of the separation spring, the spindle rotates clockwise, on the one hand, the piston moves upwards through the crank slide mechanism, compressing the gas. On the other hand, two sets of four-rod drive system make the main gate knife open first, then push the arc cutter to open the arc contact, the compressed air in the cylinder through the vent to extinguish the arc.