Payment & Shipping Terms:
|Work Voltage:||110V/220V||Rated Current:||15A|
DXN-5T High Voltage Indicator with Sulphur hexafluoride Switchgear equipment
High voltage electric display devices using neon lamps as display elements are widely used in distribution cabinets. After a long period of operation, a high loss of visibility and extensive damage to neon bubbles are found. In order to compensate for the defect, a neon light running / closing switch was installed on the electric display device, which was in a state of turning off at normal times, thus temporarily deactivating the whole high-voltage electric display device.
This treatment loses the role of a high-voltage live display device as a monitor for whether the line side is charged.The brightness of neon lamps is low, especially in bright environments where the brightness is scoured and less visible.The old type of high-voltage electric display device with mandatory electrical latching, which is too simple in principle, consists of half wave rectifying and directly combining the signals from the A, B and C phase sensors to control the latching circuit. In this way, when the system has an anomaly of single phase grounding or absence phase, the drift of the locked-in control voltage can lead to the accident of the electrically connected grounding switch.
|Rated voltage (KV)||3.6||7.2||12||24||40.5|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||25||32||42||68||100|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||40||60||75||125||185|
|Local discharge (pc)||≤10|
Contact Person: Cheng