Payment & Shipping Terms:
|Material:||Epoxy Resin||Rate Voltage:||12 KV|
|Flexural Strength:||8 KN||Color:||Red/Brown|
epoxy resin cast insulators,
cast resin insulator
CHN3-12Q/190 1600A 10kV Epoxy Resin Insulators Contactor Box Switchgear Spolt Bushings
1. Material: Epoxy resin
2. Function: mainly used in the switchgear for insulation
Insulator is the special part to fix,install and insulat on communication, electric power, lightning protection, machinery, medical, wind energy, frequency conversion equipment,new energy vehicles (integrated chassis cabinets, locker, etc.) to provide meet the fixed support, installation and insulation isolation effect of special parts, it is also known as insulators, insulation column .Its appearance is usually the cylinder,hexagonal,round.
1.The APG process includes three processes: pre-mixing, automatic pressure gel, and solidification after molding.
2. APG process equipment mainly includes mould, Pre-mixing capacity, mobile injection special pressure vessel, full hydraulic automatic pressure gel molding machine, air compressor, after solidification need oven and necessary auxiliary machine.
3. In pouring, pouring material is the key. It has a great influence on the reliability and stability of cemented pole. For example, Xiamen H Electric Switching Co., Ltd. uses the resin materials of Vantico, Switzerland, and adopts different formulas according to different current, etc. to meet different working conditions. For example-40 ℃-250 ℃.
4. The solid seal column uses the APG technique, the automatic pressure gel molding of epoxy resin. It can shorten the production cycle of epoxy insulation from ten hours to ten minutes, and can control exothermic effect well. It can compensate the shrinkage caused by curing reaction, and has excellent dimensional stability and high mechanical strength. Especially applied to vacuum circuit breaker sealing pole column, complex, thin wall, multi-directional core extraction products are more advantageous.
5. Through the cabinet drive mechanism and circuit breaker chassis car to achieve the electrical operation of the "five-prevention" function. Under some new electrical conditions and operation mode, the part of "five-guard" function in the cabinet can not meet the requirements, and the "five-guard" function must be improved.
|Item||Name||Rated voltage (KV)||Rated frequency(Hz)||Frequency withstand voltage 5 min (KV)||Local discharge (pc)||Creep distance (mm)||Dispute bend (kN)||Lighting impulse withstand voltage (KV)|
|4||Contactor box (1600A)||12||50||45||≤10||＞240||≥8||80|
Contact Person: Cheng