StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
APG Technology Epoxy Resin Bushing 3150A 10kV for Handcart Type Switchgear
|Material||Casting Resin , Epoxy Resin||Rate Voltage||12 KV|
|Frequency Voltage||42 KV||Current||3150A|
|Creepage Distance||240mm||Flexural Strength||10 KN|
epoxy resin cast insulators,
CHN3-12Q/250 3150A 10kV Epoxy Resin Insulators Spolt Bushings
We are specialty on epoxy resin medium voltage and high voltage components, such as 10KV, 24 KV and 40.5KV Circuit Breaker , Load breaker switch , Disconnecting Switch , Epoxy resin switchgear bushing , contactor box , insulators and transformer . 630A, 1250 A ,2500A , 3150A and 4000A contact box , club contact , fix contact, arm contact and jaw contact . 630A and 1250A VS1 circuit breaker . 630A and 1250A ZN85-40.5 circuit breaker . 12KV and 24KV earth switch. KYN28A-12 and KYN61 high voltage switchgear components .
The contact box is the pressure gel molding structure of epoxy resin APG process, which is used for various kinds of handcart type switchgear, acting as insulation isolation and connection transition.
The contact box is formalised by ecoxy with APG technologies, it is used for integration and conversion of various switch trucks.
Because the circuit breaker has been in the middle, so called the armor type to move the type of metal closure switch equipment, short for the cabinet. (2) The central cabinet is a type of switchgear used by end users. It is fully functional and large in size, while the ring cabinet is a type of switchgear used to connect two power sources or parts of a ring network. The main function is to divide the two sections into two parts. There are many kinds of lockers, which can be divided into the switchboard, the measuring cabinet, the transformer cabinet, the change cabinet used, and so on. The switch in the cabinet may be equipped with an automatic protection device.
|Item||Name||Rated voltage (KV)||Rated frequency(Hz)||Frequency withstand voltage 5 min (KV)||Local discharge (pc)||Creep distance (mm)||Dispute bend (kN)||Lighting impulse withstand voltage (KV)|
|3||Contactor box (1250A)||12||50||45||≤10||＞240||≥8||80|
|4||Contactor box (1600A)||12||50||45||≤10||＞240||≥8||80|