Epoxy Resin Insulator
Medium Voltage Insulators
High Voltage Epoxy Resin Insulator
Vacuum Circuit Breaker
Epoxy Resin Bushing
Electrical Switchgear Components
Cast Resin Transformer
Copper Electrical Contacts
High Voltage Disconnect Switch
Zinc Oxide Lightning Arrester
Industrial Cable Ties
Electrical Conduit Plastic Pipe
High Voltage Indicators
Moulded Case Circuit Breaker
StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
JYN2-35kV 1250A High Voltage Epoxy Resin Insulator Spout Bushing White Color
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Rate Voltage||40.5kV||Frequency Voltage||100kV|
electrical post insulators,
high voltage post insulators
JYN2-35kV 1250A Spolt Bushings Insulators with Indoor High Voltage Switchgear
First, use the electric car. Before the grounding switch, pull the circuit breaker car out of the cabinet, then push into the electric check car, the circuit grounding switch after checking that there is no voltage.
Second, open the door. When the circuit breaker is in the test position and the charged display device detects that the line has no voltage, turn on the door and check that there is no voltage, then close the ground switch.
Third, depending on the line side electric display of the role of locking device. As long as the line side electric display latching device indicates no power, latching open, the operation of the grounding switch.Method A large amount of operation, equivalent to no electric car power outage operation, only bus and grounding operation, the use of special electric car and ground hand car. Method 2 is adopted by some power departments, the operation procedure is complicated.Methods The third method is to use a more common way. When the circuit breaker is in the test position, the grounding switch can only be met if the circuit side has no electricity and the electric display device is electrically and normally, and the locked electromagnet is electrically and normally. Any failure or loss of power in a live display device or locked electromagnet will not be able to close the gate. At present, there are no accidents of electrically connected ground switch due to locking fault of electric display device. When the charged display sensor fails or breaks, it is reflected through the indicator light on the charged display.
|Rated voltage (KV)||40.5|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||100|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||185|
|Local discharge (pc)||≤10|