Payment & Shipping Terms:
|Name:||Earthing Switch||Voltage:||High Voltage|
|Space Dsitance:||210mm||Space Current:||31.5kA-40kA|
|Short Circuit Opening Current:||80kA||Life:||2000 Times|
high voltage earthing switch,
earth switch in switchgear
High Voltage Earthing Switch For Earthing Protection 2000 Life Times
1, Ambient air temperature limit: +40, lower limit: -20 degrees centigrade
2, The altitude is not more than 1000mm. If more than 1000mm, please indicate when ordering;
3, The average daily value of relative humidity is not greater than 95%, and the average monthly value is not greater than 90%;
4, The intensity of the earthquake is not more than 8 degrees;
5, Pollution class: II
The Indoor high voltage Eartihng switch JN15-24/31.5 is new design type earthing switch . The design of advanced structure is simple and the technical performance is reliable , fit with standard GB1985-2004 <AC voltage load breaker swith and earthing switch > and standard IEC62271-102; 2002 . Lend itself to power systerm with indoor 24kV three phase alternating current 50(60)Hz .
It can protect so many electrical equipments , and concurrent use with so many switchgears . Altitude is after 1000M . (Compared with the permanent magnetic type, which is mainly the control and operation mechanism, the fixed seal type is the projectile type, and the permanent magnetic type is the controller) The whole cabinet is called the armor type moving medium metal closure switch equipment, which is divided into three layers, the upper layer is the bus and the instrument panel(separate), the middle layer is the circuit breaker room and the lower layer is the cable room. Because the circuit breaker has been in the middle, so called the armor type to move the type of metal closure switch equipment, short for the cabinet. (2) The central cabinet is a type of switchgear used by end users. It is fully functional and large in size, while the ring cabinet is a type of switchgear used to connect two power sources or parts of a ring network.
The main function is to divide the two sections into two parts. There are many kinds of lockers, which can be divided into the switchboard, the measuring cabinet, the transformer cabinet, the change cabinet used, and so on. The switch in the cabinet may be equipped with an automatic protection device.
|Rated voltage (KV)||24|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||68|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||125|
|Local discharge (pc)|
|Dispute bend (N)|
Contact Person: Cheng