Epoxy Resin Insulator
Medium Voltage Insulators
High Voltage Epoxy Resin Insulator
Vacuum Circuit Breaker
Epoxy Resin Bushing
Electrical Switchgear Components
Cast Resin Transformer
Copper Electrical Contacts
High Voltage Disconnect Switch
Zinc Oxide Lightning Arrester
Industrial Cable Ties
Electrical Conduit Plastic Pipe
High Voltage Indicators
Moulded Case Circuit Breaker
StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
1000mm Secondary Socket Interlock Mechanism Between Circuit Breakers
Secondary Socket Interlock,
1000mm Secondary Socket Interlock,
1.4M High Secondary Socket Interlock
Secondary socket interlock mechanism Between Circuit Breakers
1. When the grounding switch is turned on, the back door of the switchboard can not be closed because when the grounding switch is turned on, a block is lowered, usually 30 to 50 cm below the switchboard, and there is a small bump on the door of the switchboard.
If the door can not be closed, the load switch can not be closed.
2. One type is mechanical interlocking, usually with a latch at the back of the load switch. When the cabinet door is opened, the latch is loaded with a spring that blocks the closing mechanism from the inside. So that it can not be protected. Close the door, and when the latch is put in, it closes.
3. This is less used now. There is also a type of electronic interlock, is in the cabinet door box on the edge of a contact switch, which is the top of the cabinet door, the load switch inside the electromagnet can start, after the start of the suction blocking mechanism, this can close.
|Rated voltage (KV)||7.2||12||24||40.5|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||32||42||68||100|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||60||75||125||185|
|Local discharge (pc)||≤10|
|Dispute bend (N)||≥10000|