StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
Switchgear Spout Epoxy Resin Cast Bushing Insulation Contact Box 10kV 2500A
|Material||Casting Resin , Epoxy Resin||Rate Voltage||12 KV|
|Frequency Voltage||42 KV||Rate Current||2500A|
|Creepage Distance||240mm||Flexural Strength||8 KN|
epoxy resin cast insulators,
cast resin insulator,
Spout Epoxy Resin Cast Bushing
10kV Epoxy Resin Insulators 2500A Contactor Box Spout Bushings with KYN28-12 Switchgear
We are specialty on epoxy resin medium voltage and high voltage components, such as 10KV, 24 KV and 40.5KV Circuit Breaker , Epoxy resin switchgear bushing , contactor box , insulators and transformer . 630A, 1250 A ,2500A , 3150A and 4000A contact box , club contact , fix contact, arm contact and jaw contact . APG Craftwork , Casting resin Material come from moulds , the temperature is 170 degree in the moulds for shapping . APG craftwork is more better than DMC craftwork . APG craftwork is light weight and clean .
(Compared with the permanent magnetic type, which is mainly the control and operation mechanism, the fixed seal type is the projectile type, and the permanent magnetic type is the controller) The whole cabinet is called the armor type moving medium metal closure switch equipment, which is divided into three layers, the upper layer is the bus and the instrument panel(separate), the middle layer is the circuit breaker room and the lower layer is the cable room. Because the circuit breaker has been in the middle, so called the armor type to move the type of metal closure switch equipment, short for the cabinet. (2) The central cabinet is a type of switchgear used by end users. It is fully functional and large in size, while the ring cabinet is a type of switchgear used to connect two power sources or parts of a ring network. The main function is to divide the two sections into two parts. There are many kinds of lockers, which can be divided into the switchboard, the measuring cabinet, the transformer cabinet, the change cabinet used, and so on. The switch in the cabinet may be equipped with an automatic protection device.
|Rated voltage (KV)||3.6||7.2||12||24||40.5|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||42|
|Frequency withstand voltage 1 min (V)|
|Lighting impulse withstand voltage (KV)||75|
|Local discharge (pc)||≤10|
|Dispute bend (N)||≥1000|