StephanQiuPu is a great electric power factory. we satisfy you very much . will cooperate with you again!
High Voltage VCB Circuit Breaker Indoor Vacuum 24kV/2500A-3150A
|Name||VCB Circuit Breaker||Voltage||High Voltage|
|Rate Current||2500A-3150A||Space Current||31.5kA-40kA|
High Voltage Vacuum VCB Circuit Breaker,
Indoor Vacuum VCB Circuit Breaker,
2500A VCB Circuit Breaker
High Voltage VCB Circuit Breaker / Indoor Vacuum Breaker 24kV/2500A-3150A
VS1 (ZN63) vacuum circuit breaker is suitable for reclosing operation and has high operation reliability and service life.
VS1 (ZN63) vacuum circuit breaker(general type) uses vertical insulators to protect against climate effects; And in the maintenance and maintenance aspect, usually only need to do the operation between or sexual cleaning or lubricating.
VS1 (ZN63) vacuum circuit breaker(pole type) adopts solid insulation structure-integrated seal pole, realized maintenance free.
The magnetic field produced by the coil and the magnetic field produced by the permanent magnet is superimposed and synthesized by the magnetic field. The magnetic core, together with the driving rod fixed on it, is operated by the synthetic magnetic force and the switch body is turned on and off at the specified speed. This mechanism is called a two-bit bistable structure because the moving iron core can be maintained without any energy consumption at the two ends of the journey. In the traditional electromagnetic mechanism, the moving core is kept at one end of the journey by the action of a spring, while at the other end of the journey, it is protected by a mechanical latch or electromagnetic energy. From the above, the permanent magnet actuator is a special combination of electromagnet and permanent magnet to achieve the traditional circuit breaker operating mechanism of all functions: permanent magnet instead of traditional .
|Rated voltage (KV)||3.6||7.2||12||24||40.5|
|Insulator(capacity)||insulating||Frequency withstand voltage 5 min (KV)||25||32||42||68||100|
|Frequency withstand voltage 1 min (V)||2000|
|Lighting impulse withstand voltage (KV)||40||60||75||125||185|
|Local discharge (pc)||≤10|
|Dispute bend (N)||≥1000|